Recently, many friends who purchase air shower rooms have asked the most questions: the principle of air shower door interlocking, and the method of resetting the air shower door failure. This time LENGE purification equipment will explain the working principle of the air shower room.
The main function of the air shower:
The working principle of the air shower room and the main function of the air shower room are dedicated passages set up for the staff to enter and exit the clean area. The air shower is a kind of purification equipment, which can effectively remove the dust on the surface of people and objects. The main function of the air shower is to reduce the amount of dust brought into the clean room. At the same time, the air shower room functions as an air lock room to prevent the intrusion of unclean air.
The working principle of the air shower:
1. The main working principle of the air shower room is to filter through the primary effect filter and the filter and then blow it to the human body for dust removal. That is, the air in the air shower room is forced into the static pressure box by the centrifugal fan through the primary air filter.
2. The working principle of the air shower room is that clean air is sprayed from the nozzle of the air shower room at high speed after being filtered by the filter. The nozzle angle can be adjusted, which can effectively blow off the dust attached to the surface of the human body or the carried objects.
3. The working principle of the air shower room. The dust blown down with the circulating air flow passes through the primary effect filter again, and cyclically reciprocates in this way to achieve the purpose of air shower.
Specification for use of air shower room:
1. Before entering the air shower room: After changing clothes and shoes, confirm whether the air shower room is in an idle state through the window of the air shower room and indicator lights. If the air shower is in working condition, do not open the air shower door forcibly and cause the air shower door lock to be damaged. After the work of the air shower room is completed, the indoor personnel leave, and the door is automatically closed for about two seconds before entering;
2. After entering the air shower room: go straight through the photoelectric sensor, and start the shower, please raise your hands in the room and then rotate the shower 360 degrees;
3. Blowing is completed: the air shower room fan stops operating two seconds after opening the door and leaving the air shower room.
4. During the air shower, the front and rear doors of the air shower room are locked. Insiders should not open it forcibly, so as not to damage the interlocking device and the door lock. If you encounter an emergency, please press the emergency stop switch, and the air shower room will stop working. At this time, the entrance and exit doors can be opened arbitrarily. During the idle period, the door of the air shower room is in an electronic interlocking state. Only one side of the door can be opened, please do not open it forcibly.
Tag: air shower room working principle,air shower room specification,air shower room function
Stainless Steel Furnishing Design, Stainless Steel Furnishing Price
The new trend of furniture: Stainless Steel Furnishing When it comes to furnitur...
Main application of PES membrane filter cartridge
Wuxi Lenge Purification Equipments Co., ltd. (briefly as “LENGE” here) in China ...
The new trend of furniture: stainless steel furniture
When it comes to furniture, wood is the main furniture material. However, in rec...
Clean room purification technology and aseptic drug filtration technology exchange meeting of pharmaceutical industry -- the successful completion of Shijiazhuang station
On November 19, Wuxi Lenge Purification Equipments Co., ltd. held an exchange me...